INTU FR WRAP L is used for fire protection of penetrations with plastic pipes (PVC, PP, PE, HDPE, PEX/Al/PEX, PE-RT/Al/PE-RT, PP-R/Al/PP-R, PP-R GLASS) running through fire partitions.
It is also possible to protect non-flammable pipes with insulation made of synthetic Armaflex /K-flex or PE foam, penetrating floors or walls.
• protection of flammable and non-flammable pipes insulated with synthetic rubber Armaflex / K-Flex or PE foam
• fire resistance up to 240 minutes
• availability: roll length: 10, 25 or 50 meters; width: 60mm and 100mm
• installation on pipes with large diameters is possible
• easy to cut
• high swelling ratio
• ideal for installation in very tight spaces
The wall must be at least 150mm thick and have concrete, cellular concrete structure or masonry structure, with a minimum density of 600kg/m3
The floor must be at least 150mm thick and have concrete, cellular concrete structure or masonry structure, with a minimum density of 1700kg/m3
The wall must be at least 125mm thick and have a steel profile structure covered on both sides with a minimum of 2 layers of boards with a thickness of 12.5mm.
Prepare the appropriate length of the tape (cut off from the roll). Wrape the pipe. Slide inside the fire partition. Fill the gap with cement mortar.
It is recommended to store in dry internal conditions at temperatures between + 5°C and + 35°C.
The cookie settings on this website are set to "allow cookies" to give you the best browsing experience possible. If you continue to use this website without changing your cookie settings or you click "Accept" below then you are consenting to this.